Nuclear Street News Team comprises of industry writers and journalist.
A problem affecting water flow in a steam generator shut down unit 3 at New York's Indian Point nuclear plant Monday.A failed valve in the main feedwater system contributed to a mismatch in the SG's steam and feed flows, according to a report filed with the Nuclear Regulatory Commission. Safety systems shut the reactor down automatically from full power. The auxiliary feedwater system actuated during the trip, the main condenser served as a heat sink, and no safety valves lifted.A release from plant operator Entergy said the shutdown at 9:15 p.m. resulted from a falling water level inside the SG after a controller failed that regulates its water flow. Unit 3 had been in service for 159 continuous days. Unit 2 was not affected by the shutdown.
how does a feed reg valve failure to control become headlined as "steam generator issue"?
I agree with the previous comment. Feed reg valve control issue does not equal "steam generator issue". It equals just what it is, a feed reg control issue. Nothing more, nothing less.
a bad feedwater reg. can trip the unit....I know... A loose feedback arm did it a few years ago.....Van